OPTION: Provide foil faced insulation in lieu of standard.Foil insulation shall meet or exceed the requirements stated above, and in addition, meet ASTM Standards C665 and C-1136 for biological growth in insulation. Insulation shall be lined with aluminum foil, fiberglass scrim reinforcement, and 30 pound kraft paper laminated together with a flame resistant adhesive. All exposed edges shall be sealed to prevent any fibers from reaching the air stream.
OPTION: Provide elastomeric closed cell foam insulation in lieu of standard. Insulation shall conform to UL 181 for erosion and NFPA 90A for fire, smoke and melting, and comply with a 25/50 flame spread and smoke developed Index per ASTM E-84 or UL 723. Additionally, insulation shall comply with antimicrobial performance rating of zero, no observed growth, per ASTM G21. Polyethylene insulation is not acceptable.
OPTION: For exposed units, the bottom access panels shall be attached with quick open fasteners to allow for easy removal and access for service.
OPTION: For exposed units, provide double deflection discharge grille and either a rear return or bottom return single deflection grille. Supply and return duct connections are available. Unit mounting shall be by hanger and slotted hanging brackets provided at four locations. For easy installation, exposed units provided with 1/2" mounting knockouts in four places.